Alright got to questions.
#1) Did a reinspection to day where I noted double taps in a panel. There solution, which is pictured, was to remove the double taps, wirenut them together and pig tail them with one single wire back to the breaker. Comments needed…
#2) On an inspection today found a panel (find a lot of them in this particular neighborhood) that had no ground wire from the panel or meter that attached to a ground rod. The realtor made the comment “Was it code at the time it was built?” Anyother time I have called this out they have fixed it without question. When did the NEC require a ground wire and what would be a good replay next time some realtor makes that comment.
Thanks in advance!