Originally Posted By: phinsperger
This post was automatically imported from our archived forum.
Simple 220V, 100A service. Not much running inside the house. Measuring the service entrance conductors with an amp meter inside the main disconnect panel just for hell of it.
Hot 5.6 Amps
Hot 3.1 Amps
Neutral 4.8 Amps
Ground 0.0 Amps
Shouldn't the Neutral be giving me a reading of ~2.5 Amps (5.6-3.1)?
Hinsperger Inspection Services
Chairman - NACHI Awards Committee
Place your Award Nominations