Quick Question : Is it normal when inspecting the main service distribution panel to notice the upper half of the breakers are warmer then the lower half?
Are you using IR? Post a photo please.
Which breakers were “under load” and which were “unloaded”?
There is no logical reason for this to happen unless the CB’s with the larger loads ended up at the top.