Tandem breakers throughout this 1979 panel. This one is double tapped with no room for more breakers. Breaker is labeled “Disposal/Dishwasher” & “Kitchen outlets”. Is there any time when a double tap is permitted? Is a pigtail repair acceptable: “The offending wires get disconnected from the circuit breaker, connected to a single wire with a wire nut, and that single wire gets connected to the circuit breaker.” Any other thoughts or suggestions?
I look forward to viewing your comments.