I have a few questions about a 30 amp fused OCPD designated for the dryer.
The one issue I observed was with a wire splice. Could this splice connector be the one that was recalled.
Now there was already a 30 amp breaker in the panel so why have the second OCPD?
Also the wire is reidentified as blue. It was not reidentified in the panel. What does blue designate?
Is it acceptable to double tap the fuse? One is incoming from the panel and one feeds the receptacle.
Please help me better understand this older wiring. I called out the fused OCPD due to the poor connection at the wire splice. I figure they could just remove the entire fused OCPD and just use the 30 amp breaker in the main panel.