Any help would be appreciated. Anyone know the maximum length insulation can be removed or visible conductor without insulation on conductor servicing a breaker.
How about a pic? There really is no rule as to how much you can’t strip. Just a little common sense. As long as it doesn’t look like it might come into contact with something…no harm will come from it.
Here is a thread from the electric section
hi all members… i just joined this forums…hope that i find this forum as great community…
Welcome Kolo. Where is Antioch?
Ironic how you joined this forum to self-promote your writing website considering your grammar is sub-par.