Should’nt the cables be on the other side of the running board? The area with the moisture stains is the attic opening.
Also I often see the grounds are installed at a larger knockout & not the small one designed for the ground wires. Is this not an issue for vermin entry?
Also if you closely at the wiring in the panel one of the wires was a different color then the rest. Why is that? I did observe more then i nuetral at each lug.
One more question. Non metalic sheathed cable is not allowed unprotected for the disposal wiring correct. My thought is it is allowed to use a rated cord for the disposer. The cord could become damaged just like the Romex right.