What do you see and how will your report read?
Consult electrician before closing of title. Mixing of copper and aluminum.
Not to mention the drywall screw through the can…
That about sums it up.
Besides the wrong mounting screw, I see branch circuit ground wires twisted together and jammed into the wrong terminal, plus the aluminum ground wire twisted around the grounding conductor but not clamped.
Call for Repair by a certified electrician.
Some one took all Joe’s pics last night
I guess he took his marbles and went home…:roll:
Here they are Mr. President:
Take your pick and apply any to your inspections if applicable, and when there are questions ask me and I will answer.
I will be lurking for a while, because I am on the road now for a few months and must keep focused, and avoid time any consuming discussions.
If any Chapter is holding a meeting, and I am in that town on that Monday or
Wednesday, let me know and I can stop in for free - just a beer will do.
See my schedule in my signature.