GAS FURNACE INSPECTION CHECKLIST
Check the following:
Adequate combustion air
Gas supply for:
a. Shut off near the furnace
b. Sediment trap/drip leg
c. Proper gas supply piping
Acceptable materials are black steel, corrugated stainless steel tubing CSST, and copper, although permissible copper varies by jurisdiction and may be limited to certain types.
d. Flex connector
Flex connectors are maximum 3 feet for furnaces and must have a shutoff where it connects to rigid gas piping. Flex connectors cannot pass through walls, floor, or ceilings, and cannot be concealed. Flex connectors may be required in areas subject to earthquakes.
Combustion exhaust venting
a. Vent material (plastic means high efficiency)
b. Vent connector proper slope (1/4” per foot)
c. If the furnace and a water heater connect to the same vent, the water heater should connect upstream from the furnace.
d. If the furnace and a water heater connect to a chimney, the water heater should connect above the furnace, and a cleanout should be installed within 6” below the furnace vent connector.
Presence of a kill switch.
Presence of a humidifier
d. Securely attached
Note the filter type (electronic/fabric), location and condition
Shut off the furnace at the kill switch
Remove the access covers
Note dirt, debris, and corrosion
11 Photograph the manufacturer’s label/ data plate
Examine the burn chamber
c. White residue
d. Loose or damaged burners
Examine the blower compartment
a. Dirty or greasy buildup on the blower vanes
For high efficiency furnaces, check for proper condensate discharge.
a. Corrosion resistant piping (ABS, PVC, CPVC, copper, (not coiled tubing) PEX, polyethylene, polypropylene).
b. ¾” minimum
c. Condensate pumps appear to be in satisfactory condition with proper electrical connections (not extension cord)
d. Trap are installed in condensate lines as required by the manufacturer.
e. Horizontal runs must slope minimum 1/8 inch per foot
f. Condensate must discharge to an approved location. Not a street, alley, or sidewalk. Check locally for “approved locations”. Most discharge to floor drains. Furnaces in attics must have a drip pan with overflow and condensate discharge to an approved location.
Turn the thermostat up high
Turn the furnace on at the kill switch
Watch for proper operation. You may need to depress the access cover safety switch for the furnace to operate.
a. The burners will ignite and run for a short time before the blower activates. Watch for any change in the flame when the blower activates. Changes in the flame can indicate a cracked heat exchanger. Recommend service. Flame color should be blue. Yellow or white flame indicates a need for service.
b. Listen to the blower. Any unusual noise indicates a need for service.
Check temperatures at registers with a digital thermometer. Comment on any that are significantly hotter or colder than the rest.