Does anyone know if these AFCI breakers are compatible with a GE panel?
I would venture to guess that is a Cutler Hammer BR AFCI. Small chance it could be Murray/Siemens but my guess is CH BR.
Don’t know about comparability, but aren’t the green button breakers replaced with a updated version? Maybe wrong color I am thinking of.
Recalled that I am aware of are blue button:
These are “Classified” breakers, as evidenced by the semi-circle around the UL logo.
Classified breakers are those that were tested in multiple panels.
These are Eaton Classified breakers, and yes, they are listed for use in GE load centers: