I wanted see if anyone can help me? I had an inspection today on townhome that hada hard wired heat detection system. All the wires in the attic were not in conduit. I work In the Chicago area where usually everything is in conduit. Is this normal for these wires? I have not come across this before now. Also in the distribution panel the breaker that is labeled fire panel has a safety clip so it can not be turned off. I this normal?
Safe At Home Inspections