What do you recommend?
I often find outlets that are Hot Neutral reversed. Sometimes GFCI’s as well. The GFCI’s function manually and power is disconnected. Testers though do not trip the circuit. Is it best practice to always recommend a licensed electrical contractor further evaluate and fix ALL Hot Neutral outlets, just GFCI’s or what?