Originally Posted By: dbush
This post was automatically imported from our archived forum.
Sorry, I don’t have a picture, but easy to describe.
2 pole (220 volt) breaker 50 amp. Black wire goes to breaker and out to outbuilding, white wire is not attached to the breaker, but is attached to the neutral bus in the panel box.
First time I have seen one that the neutral wire on a 2 pole breaker is not attached to the breaker itself.
Is it wrong or just different?
"LIFE'S TOUGH, WEAR A HELMET"