New service installed on this 4500 SQ footer 100 amp main breaker at the new meter base. I am not the sharpest pencil in the box but this just ain’t gona work:shock:
I would guess that the 117 amps isn’t sustained for very long otherwise the 100 amp CB would eventually trip. Where is the GEC?
The 117 amps was on the breaker for several minutes until I quit juicing it and it never did trip. GEC was next door on the meter base;-)