Family, I came across the attached panel today in a condo. It was run underground, and the panel was on the interior side of the exterior!meter. Out of curiosity, what type of panel is this?
That appears to be a service panel (main). The 6 upper breakers are all required to be shut off to disconnect all power. This meets the 6 handle rule. The panel is a split bus panel and the lower 60A 2 Pole breaker on the right controls power to all of the lower single pole breakers. I dont see a bond screw but that doesn’t mean there isn’t one there.
There were several issues with this panel, and thanks for assistance bro!