Came across this this morning and I am not sure how to report it mostly because I have not encountered it before.
The meter is a fairly recent installation. The panel below has no main disconnect within the panel, and the dual pole 50 Amp breaker above is labelled as the main disconnect and the connections are set up as such (from the meter, to the 50A, to the main lugs in the panel.
a) Is this set up kosher? I cannot immediately find any reason it would not be, but I also do not know the NEC inside and out.
b) Is the 50A breaker large enough? It doesn’t seem to be, but I am also looking for some source to cite to support that assessment.