Found this configuration the other day. Main disconnect, which is pictured up close in the first photo, has three conductors feeding separate panels. What possible issues do you see?
Non-compliant triple taps!!
Wow that’s a rip it out and start over.
Turn power OFF 1st!
All bad. It’s a do over
Since no one asked
What is soooooo bad? besides the obvious double lugging? let’s see a list so we could all learn.
Let’s start with the SEU cable using 3-wire feeders.