I’m looking for some advice on this sub panel.
So far I have noted in the report: Surface wiring, the feed for this panel is double tapped in the main panel, grounds and neutrals should be separated.
Is this correct?
What else is note worthy?
This sub panel feed a time of use device (from the utility) for the a/c unit.