Had a service disconnect outside that only used load wires and no neutral. The ground was in the meter base.
Inside was a standard panel with additional service disconnect and they wired it with isolated grounds/neutrals and removed the bonding bar at the bottom.
Whats the best way to remedy this one? I figured just re-bond both busses should correct, and the original disconnect would be irrelevent.