This service is in need of upgrading.
Please follow the pictures and comment as applicable.
The main in the garage was improperly labeled they had the A/C pullout were the main was supposed to go.
Then it feed to a 50 amp FPE breaker that feed to a FPE fused panel and then a separate 30 amp shut off for the dryer.
There is an old unused heater in the garage with the electrical in disarray.
The interior had mislabeled GFCI protected receptacles, handyman wiring under the counter and a dimmer and GFCI for the microwave. (Not so sure of this setup)
The phone, cable and antenna wiring looked like a 1st grader installed. The phone plug on the shelf is a good one.
Please review the pics as I will post as many as I can.
In one of the Pics there is a receptacle on the opposite side of the sink within 6ft. I suggested GFCI protecting.