Originally Posted By: jpope
This post was automatically imported from our archived forum.
Okay, we’ve determined through previous topics that the neutral is not to be “regrounded” after the service with the exception of separate buildings that do not have a parallel metal path to the first building.
Does this "parallel metal path" refer to the conduit and/or the EGC? And does this mean that the presence of the "pmp" requires an isolated neutral even in a separate building?
JPI Home Inspection Service
"At JPI, we'll help you look better"