I don’t like how they double lugged the service wire in the main panel to install the sub panel. Any thoughts on this?
Its wrong, easy fix will take about 10 minutes to fix
It’s incorrect because that neutral terminal is not listed for two conductors. Also the neutrals need to be re-identified as white or gray not black.