Originally Posted By: rmoore
This post was automatically imported from our archived forum.
Not just you Joey! Unfortunatley all too common lazy install. No way of knowing if all the EGC’s are secure. The lug below also has a “double tapped” neutral (with the GEC). None of this is probably a huge safety issue assuming good contact, but “probably” isn’t good enough and we all know “assuming” is dangerous.
Yeah, I'd recommend the EGC's be moved to individual lugs (or two or three depending on the panel listing). The double tapped neutral also needs its own lug.
Rest Assured Inspection Services