This is a two part question:
There is one service panel and one sub panel. According to the labels, both panels are rated at 125 amps maximum. The service panel has one 100 amp breaker (common int trip) and one double pole 40 amp. The sum of all the breakers in the subpanel exceeds 300 amps. Am I missing something and should I call both of these out as undersized.
My reporting software has a rec for service “substantially” less than 200 amps to be upgraded. What is the opinion out there for making this rec in this case? The two wires from the 100 amp breaker to the sub are 1 AWG AL; I could not read the rest but the SEC looked like 1/0 AL