Originally Posted By: jrabanus
This post was automatically imported from our archived forum.
This place was a nightmare. The pictures are a little fuzzy so please bare with me. The first picture show the SEC off the meter going into a main switch, but also there was a another SEC coming off the meter going into a breaker panel with no main switch. (which is the second picture) The second picture shows this breaker panel had EXPOSED WIRING THAT WAS HOT!! Also it had a double tap. Then in a crawlspace they had wiring that was hot just hanging there. Needless to say I told them to get an electrician out there now.