Originally Posted By: tthompson
This post was automatically imported from our archived forum.
I would like to hear your thoughts on this set-up
The dryer was moved out to the garage.
The location for the old dryer was made into the bachelor suite.
The panel had one 40 amp breaker and one 30 amp breaker.
Upstairs kitchen had a stove as well.
The stove in the bachelor suite is hooked up to the old dryer plug. Both the dryer and stove in the suite seem to be run parallel with each other...
There was no double lugging in the panel.
I called for an electrician to check over the Harry Handyman wiring.