Originally Posted By: pdacey
This post was automatically imported from our archived forum.
I love inspecting out in the county where there is no AHJ or codes.
Sub panel in detached workshop. All breakers are 30 amp wired to #12 awg. Top 3 breakers on the right are all double tapped. Grounds and neutrals on common bus and feeder cable enters building and panel unprotected.
[ Image: http://www.nachi.org/bbsystem/usrimages/I/IMG_3931.JPG ]
[ Image: http://www.nachi.org/bbsystem/usrimages/I/IMG_3932.JPG ]
[ Image: http://www.nachi.org/bbsystem/usrimages/I/IMG_3934.JPG ]
...and this was the lighting. About 10 of them.
[ Image: http://www.nachi.org/bbsystem/usrimages/I/IMG_3938.JPG ]