Is it correct for a subpanel neutral and ground be on the same bus bar ?
No they need to be separate anywhere beyond the service disconnect.
Thank You, Just what I thought. I’m glad I caught this one
Also what is up with the terminal adapter for the feeder cable being reversed? Did they have bare wire coming in or a coupling and a PVC nipple?