I was in the middle of an inspection when I used the sutre test 61-165 on the outlet in the bathroom. I tripped it with the tester and went to reset it. when I retested it it was blank and I tried it on other outlets . . . nothing.
Have any of you had similar things happen with your tester? I’d hate to see $450 bucks go down the tube.
Mahalo for your help