Originally Posted By: bbadger
This post was automatically imported from our archived forum.
Here are some photos I have taken at work lately, they show that poor electric work is not limited to houses.
This first one is a 200 amp, 3 phase 208Y/120 panel supplied with 12 AWG.
Click on the above photo for larger image.
This next one is a 225 amp, 3 phase 208Y/120 panel in this one we have 'double tapping' issues.
Click on the above photo for a much larger image.
Click here for a large overall shot of the panel just above.
This last one is another 225 amp 3 phase panel that has been in use for 2 or 3 years but no one ever tightened phase A of the supply conductors into the breaker.
Questions and comments are welcome.
Electrical Construction & Maintenance
Moderator at ECN