Guess you do not care for radiant floor heat.
Good one Bob… This was in a room off the Garage…
I like the stick man in flames graphic :twisted:
Inadequate combustion air too, unless that room is bigger than it looks.
I liked it too Chuck and all three pictures were included in the report.
There was a vent in the non airtight door and the room was larger than the it looks.
one square inch per 1,000 btu and should have a top vent to match that bottom in your picture.
Was the room accessible only *through *the garage (which makes it part of the garage)? Looks like the TPR goes into a crawl space. I never saw a garage on a crawl space. Missing a pan, for sure, but no elevation is required unless it’s considered to be a garage.