I reffered the boxes to a sparky and was concerned about the double taps and the main feeding a 60 amp fuse and then going to a 100 amp sub.
No seperation of nuetral & grounds.
They also feed the garage with a non rated wire for burial and the sub in the garage was about 8 feet high. They also mixed 10 gauge and 12/14.
Is there anything else in the pics that you may see that I might need to know.
It also appeared only a water ground and no exterior rod.