Need a little help here. This is a picture of an AFCI breaker that looks like it is double tapped and real hot. It’s a 15 amp breaker running 3 bedrooms upstairs and 1 downstairs in the finished basement. (extra wire). Can someone let me know if this is a problem?
Jeff inspector in Colorado