Originally Posted By: jonofrey
This post was automatically imported from our archived forum.
Some time ago, I called out a 40 amp breaker connected to 10 AWG copper. The electrician that installed the panel called me to say that depending on what the circuit is serving, he could bump up the breaker size.
That's news to me? When I check conductor size I've always referenced NEC 310-16.
What's up with that?
BTW - please look me in the eyes and quit staring at my breasts. ![icon_lol.gif](upload://zEgbBCXRskkCTwEux7Bi20ZySza.gif)
We're NACHI. Get over it.