I removed the image because an inspector said it was over the head of a home inspector…i disagree but since a post I felt was valuable as a lesson is commented that is not for HI’s so it’s gone…and I’m gone as it seems folks above education anymore.
Now I will chat only with my electrical brother…
Robert my friend. The change was really just a clarification to a rule that already exists…just placed in the wrong place within 215.2. This change clarifies that adjustments and corrections will apply and it also acknowledges that without a connection to limiting devices like OCPD’s the actual current is what it is…and the conductors are indeed acceptable where sized to handle 100% of the continuous and 100% of the noncontinuous as you know.
Anyway…future images will be available on my website for those will choose to enjoy them. I mainly posted it so that someone may comment on the violation in the actual image…but it’s all good. Peace folks.