Originally Posted By: pabernathy
This post was automatically imported from our archived forum.
Firstly, I personally think using the jacket on the romax to label a panel is (1) crappy and (2) not needed. In our area that would fail just for spite by most of the " CITY " inspectors. ( You know how much power the AHJ has…lol )
Secondly, I also do not ever recall in my nearly 20 yeas in the electrical business ( even in older wiring ) where I have seen a neutral and ground connected to a breaker.....heck my 7 year old son would not do that..lol
Anyway...something has to be missing from this image...just not sure what....maybe they just turned them the wrong way and they are not terminated on anything...who knows...
But Bob is right......I agree..." Whats up with that...lol "
Paul W. Abernathy- NACHI Certified
Electrical Service Specialists
Licensed Master Electrician
President of NACHI Central Virginia Chapter
Moderator @ Doityourself.com
Visit our website- www.electrical-ess.com