Originally Posted By: jpope
This post was automatically imported from our archived forum.
If the upper half is protected by that two-pole breaker (cannot make out the amps) then that ugly alum connection is just an un-fused circuit?
It's difficult to see that it is a split bus, but closer observation seems to have confirmed that.
I assumed that these were the SE cables.
Are all of the upper circuits 240 amps? I can't see the handle ties if so.
JPI Home Inspection Service
"At JPI, we'll help you look better"