Originally Posted By: ssmith3
This post was automatically imported from our archived forum.
New construction (still working on it). GFCI outlets on rear decks. Plug in Suretest and the thing trips (happens on all of them). I reset it and got a wiring OK. I then checked voltage drop 13% . This was not the furthest outlet from the panel. I checked the furthest and there was only 1.1%.
What should I call out? "Outside GFCI receptacles appear to be faulty. Recommend further evaluation by a licensed electrician."
Vice President NorCal NACHI Chapter
I graduated from collage. Now my life is all mixed up.