I need some help on clarifying this one. Service comes down utility pole in the alley to the meter then to the disconnect directly below it. From the disconnect, it goes back up the pole, then overhead to the house about 100’. At the house it comes down the wall, to a “junction box” where it connects to the conductor that finally makes connects it to the panel in the house.
Is the 3-wire feeder okay in this situation? The house panel is still the distribution panel, right, and therefore would need the grounded and grounding conductors separated?
It doesn’t appear to me that the distribution panel is bonded or grounded correctly, but wanted to make sure I communicated it correctly in the report. Thanks.