This isn’t a problem with an inspection, rather it is with my own home. I went to replace a dimmer switch this morning and it had 2 black wires going to the dimmer switch. It is my understanding that one of these should be a line wire and the other a load. With this particular previous installation, both wires had voltage going to them. Does this sound right to anyone?