Please see photos, point of sale no issues, 2 panels updated.
Service old, 60 amps, feed 2 meters.
My questions are is this 1 60 amp feed to 2 100 amp panels or 2 60 amp feeds to 2 100amp panels?
old 60 service feeds 100 amp FPE, then wires are spliced 2 to 100 amp panels, now these would be considered subs, not mains correct.
The city guy should be able to tell SEC is undersized at mast correct? I know they do not take off panel covers (seems a disservice to me)
Obviously this is not safe & is called out but questions above would be appreciated.
Seems they did this way so they did not need to update exterior & GEC.
Pics are of the exterior service, one main panel. Next post are the 2 remote distributions, not mains correct???
The blurry picture is the surface wires at the main breaker. (60 amp SEC to 100 amp FPE)