Originally Posted By: Ben Gromicko
This post was automatically imported from our archived forum.
Today I inspected a house with an overhead 200-amp main electrical service line entering the electrical meter box. The 200-amp line continued from the meter to the house electrical panel box. All well.
However, when I inspected the main electrical disconnect, it was labeled 150-amps.
What da F?
Benjamin John Gromicko
NACHI & ASHI Member