Would you call this a proper drip loop in the service wires (New panel had no signs of any water entry)
Definitely not the top one. Lower 2 I would classify as ‘barely’ a drip loop.
two out of three…
I may have pushed down on the neutral, with my rubber pusher downer enough to make it okay.
DO NOT TRY THIS BECAUSE OF A SAFETY HAZARD!
you have a rubber pusher downer ???
I would call it. Barely a loop. Also looks to be graspable within 3’ of an operable window.
Sue, it doesn’t count if it is above the window.
Doesn’t everyone carry a rubber push downer??!!