I always enjoy reading the message board and I’m amazed at the knowledge here. I have a question in regards to an entrance cable size / breaker size.
The cable coming in said 2 awg and is approximately 3/8". There is a 200amp main disconnect at the bottom of the panel, with the neutral connected but the two hot cables are connected to a 100amp circuit breaker with a sticker stating main breaker. That’s due to the wire size that it can’t be in the 200amp main disconnect? How can I tell if the main service will accept a 200amp panel? The meter has 200CL but the cable size appears lacking.
Any help would be appreciated!