This is my home but wanted to post as most do not pull off covers as it is not required in a non invasive inspection but I have the following improper electrical practices.
exterior light with no visible junction box and lacks ground connection.
updated lights and switches lacking the ground connections.
So if you were doing an inspection on an older home and was noticing some open grounded outlets would you also mention the lack of a ground at the lights and switches if they had been modified?
Also did an inspection for a client how lived in the home and they used drywall screws to secure the receptacle to the outlet. I would not of known if he did not tell me as he lived there. (Last pic)
I added a exterior box designated for a wet location but it stall lacks a ground.