Originally Posted By: jtedesco
This post was automatically imported from our archived forum.
NEWS from CPSC
U.S. Consumer Product Safety Commission
Office of Information and Public Affairs Washington, DC 20207
FOR IMMEDIATE RELEASE
November 3, 2004
Release # 05-035 Firm?s Hotline: (877) 202-9046
CPSC Consumer Hotline: (800) 638-2772
CPSC Media Contact: (301) 504-7908
CPSC, Schneider Electric North American Division Announce Recall of AFCIs
WASHINGTON, D.C. - The U.S. Consumer Product Safety Commission announces the following recall in voluntary cooperation with the firms below. Consumers should stop using recalled products immediately unless otherwise instructed.
Name of product: Arc Fault Circuit Interrupters (AFCI)
Units: About 700,000
Manufacturer: Schneider Electric North American Division, of Palatine, Ill.
Hazard: An AFCI is an electrical circuit protection device (circuit breaker) that detects electrical arcs from cracked, broken or damaged electrical insulation and shuts off power to the circuit before the arcing leads to a fire. An electronic component failure inside the AFCIs can cause the devices to not detect an electrical arc. Although the AFCIs will function as regular circuit breakers, they may not detect an arc fault, posing a safety risk to consumers.
Incidents/Injuries: Schneider Electric is investigating one reported fire during a new home construction that may be related to this problem. No injuries have been reported.
Description: The recalled Square D QO? and Homeline? Arc Fault Interrupter circuit breakers are used with 15- and 20-amp branch circuits. They are required to be installed in bedroom circuits in accordance with the 2002 National Electrical Code.
The recalled units were manufactured after March 1, 2004, and have a blue test button.
The AFCI circuit breakers have one of the following date codes ? CN, DN, EN, FN, GN, HN, or JN ? stamped in red on the breaker label located just above the wiring terminal.
The recalled units also have one of the following catalog numbers printed on a label on the front of the breaker: QO115AFI, QO115AFIC, QO120AFI, QO120AFIC, QOB115AFI, QOB120AFI, HOM115AFI, HOM115AFIC, HOM120AFI, HOM120AFIC, QO115VHAFI, QO120VHAFI, QOB115VHAFI, or QOB120VHAFI.
Sold at: Electrical distributors and retailers sold the AFCIs between March 2004 and September 2004 for between $30 and $130.
Manufactured in: Mexico
Remedy: Installed AFCIs will be replaced free of charge through electrical contractors. Consumers can return uninstalled AFCIs to the retailers or distributor from whom the unit was purchased for a free replacement unit.
Consumer Contact: Consumer should call Schneider Electric toll-free at (877) 202-9046 between 7:30 a.m. and 5 p.m. ET Monday through Friday or log on to the company?s Website at www.us.squared.com/recall/AFCI
QOAFI CIRCUIT BREAKER HOM CIRCUIT BREAKER
Test Button is BLUE on Recall Circuit Breakers
Send the link for this page to a friend! The U.S. Consumer Product Safety Commission is charged with protecting the public from unreasonable risks of serious injury or death from more than 15,000 types of consumer products under the agency's jurisdiction. Deaths, injuries and property damage from consumer product incidents cost the nation more than $700 billion annually. The CPSC is committed to protecting consumers and families from products that pose a fire, electrical, chemical, or mechanical hazard or can injure children. The CPSC's work to ensure the safety of consumer products - such as toys, cribs, power tools, cigarette lighters, and household chemicals - contributed significantly to the 30 percent decline in the rate of deaths and injuries associated with consumer products over the past 30 years.
To report a dangerous product or a product-related injury, call CPSC's hotline at (800) 638-2772 or CPSC's teletypewriter at (800) 638-8270, or visit CPSC's web site at www.cpsc.gov/talk.html
To join a CPSC email subscription list, please go to www.cpsc.gov/cpsclist.asp
Consumers can obtain this release and recall information at CPSC's Web site at: www.cpsc.gov
Joe Tedesco, NEC Consultant