Originally Posted By: pdacey
This post was automatically imported from our archived forum.
50 year old house, original disconnect is below the meter. One more disconnect panel has been added more recently to the left of the meter. The feeds to the panels come from the connections inside the box below the meter, as well as the connection to the service neutral. The newer panel to the left does not have a grounding conductor attached to an electrode. The older panel below the meter does. Is this OK since they are connected to one another inside the junction box?
[ Image: http://www.nachi.org/bbsystem/usrimages/I/IMG_0815.JPG ]
[ Image: http://www.nachi.org/bbsystem/usrimages/I/IMG_0818.JPG ]