Is a Grounded conductor terminations and Neutral conductor terminations the same in respect to the issue below?
The reason I ask is because I have a neutral bar with many double tap and am going to write it up as an issue.
Just looking for clarification.
But reading NEC 408.41 it refers to Grounded Conductor Terminations.
408.41 Grounded Conductor Terminations. Each grounded
conductor shall terminate within the panelboard in an individual
terminal that is not also used for another conductor.