All the years I’ve been doing inspections, I’ve never ran into this situation.
Ok…Here’s the situation. See the picture below.
“Click To Enlarge”
I have several 50 Amp metered panels wired into a 200 Amp service. There is only one (1) main disconnect (Long Handle) at the main SE panel. This will shut down the entire building. The other smaller metered panels do not contain main disconnects per panel and there are no other main disconnects anywhere for these individual smaller panels.
Are these considered to be sub-panels/load side equipment, where all the grounds should be bonded?
And aren’t individual shut-offs required somewhere, for these smaller panels?