Originally Posted By: Russell Frame
This post was automatically imported from our archived forum.
Installing a new service panel and have a quick question.
Is it a no-no to double tap the grounding lug on the ground bus with the cable that's being used to bond the neutral bus?
I'm assuming it is not ok and that a seperate lug should be used or a bonding clamp should be connected to the ground cable directly...